Differential pressure switch, also called differential pressure controller. The installation and construction principle of differential pressure switch can be divided into mechanical differential pressure switch and electronic differential pressure switch. Electronic differential pressure switch needs power supply to work, and their wiring diagram is different.
Then, how to wire the mechanical differential pressure switch and how is the wiring diagram of the electronic differential pressure switch?
As shown in the figure above, the picture on the left is the wiring diagram of mechanical differential pressure switch. Without power supply, you can directly connect the normally open signal (NO + COM) or normally closed signal (NC + COM) to the equipment
The right part is the wiring diagram of the electronic differential pressure switch. The electronic differential pressure switch is a relatively high-grade instrument compared with the mechanical differential pressure switch. It can have two output switch signals, but it must be powered all the time to work. As shown in the figure, he has two couples of switch signals, SPDT single pole double throw switches, or can also be used as DPDT signals. At the same time, DC24V + DC24V - is introduced into the terminals marked with + - respectively. Do not connect them reversely or mistake them with 220V power supply, otherwise the differential pressure switch will be burnt and directly discarded.
Recommended Differential Pressure Switches:
A.YITE Brand 101NN type Mechanical Dfferential Pressure Switches
Higher static Pressure, Large adjustable range
No need Calibrate, Easy adjust by pressing the button, easy installation, 2 set point, 2 SPDT switch, adjustable. Made by A.YITE TECH, GE-209 series
Add: Building 17 &22, No.2928, Chuan Zhou Highway, Shanghai, 201319, China